# Energy Vanguard Blog

### Size Matters — How Big a House Can You Test with One Blower Door?

I get asked variations of this question often enough that it's worth addressing here. If you're doing a blower door test, how big a house can you test with one fan? Or, put another way, how many blower doors do you need to test a really large house? That question has no answer because it's based on a faulty premise.

### Does size matter?

Yes, it does. But it's not the size of the house that matters. It's the size of the hole in the house. You could have difficulty pressurizing a 3000 square foot house to 50 Pascals (Pa) with a blower door. Alternatively, as HERS rater Eric Griffin learned yesterday in the PHIUS+ Rater Training at the RESNET conference in Orlando, you might be able to get a 40,000 square foot house to 50 Pa using the much smaller Duct Blaster fan.

There are two problems with asking how big a house you can test with one blower door fan:

1. The amount of leakage scales with the area of the building enclosure, not the conditioned floor area (and certainly not with the volume).
2. Every home has a different amount of leakage per square foot of building enclosure.

If, on the contrary, leakage increased with the amount of conditioned floor area and every home had the same amount of leakage per square foot of floor area, then the question would be valid. They aren't, however, so it isn't.

### What's the flow rate?

If a 3000 square foot home has an infiltration rate of 10,000 cfm when the pressure difference across the house is 50 Pa, one blower door fan will not get the house to 50 Pa. The Minneapolis blower door can get up to about 5300 cfm at 50 Pa (cfm50). The Retrotec Q46 can go up to about 5600 cfm50, so you'd need about two of either type. (You can still get a cfm50 even without getting a 50 Pa pressure difference, though, because of the cool mathematical property known as extrapolation.)

The 40,000 square foot house that could be tested with a Minneapolis Duct Blaster fan, however, must have had an infiltration rate of only 1000 cfm50 or so, the limit of what those fans can do.

The cfm50 doesn't tell you if the home is leaky anymore than my telling you I have a 230 pound friend tells you if he's fat. 1000 cfm50 could be really leaky if we're talking about a really small house, or it could be amazingly tight in the case of the 40,000 square foot house. That's where air changes per hour (ACH50) and cfm per square foot of building enclosure area come in. By normalizing to the size of the house, you can decide if it's leaky just as if I tell you that my 230 pound friend is 6'6" tells you he's not fat.

Speaking of testing homes with duct tester fans, I did that last year in a net zero home near Memphis, Tennessee.

### Upshot

A really small house might be really leaky and need more than one blower door fan to get a 50 Pa pressure difference. A really big house might be really airtight and need only a tiny fan to get a 50 Pa pressure difference. How big a house you can test with a blower door depends on how much air you need to get the 50 Pa pressure difference.

Related Articles

Infiltration Occurs at the Surface, Not in the Volume

A Blower Door Can't Tell You How Much Mechanical Ventilation You Need

A Fun Visualization of Air Leakage During a Blower Door Test

A Net Zero Energy Home in Rural Tennessee

Our Model Q4E that we now call the 3000 will go to 8000 CFM and test just about any house.
Posted @ Tuesday, February 26, 2013 1:12 AM by Colin Genge
Colin: One could also easily daisy-chain two US 1000s to get an even greater CFM, and perhaps at even slightly less cost, correct?

Allison: So the size of a house is irrelevant to leakage in the presence of an army of gnawing squirrels, right? I just need to be sure about this... :-)

~John
Posted @ Tuesday, February 26, 2013 6:52 AM by John Poole
Allison,

Also, the DG-700 manometer (and I'm sure other models) has the '50pa' mode which extrapolates current flow rates to a projected CFM50.

Now, I've never seen any data as to what the variance from a true 50 pa test would be, but that does help bridge the gap.

Erik
Posted @ Tuesday, February 26, 2013 7:51 AM by Erik North
The money spent on testing is much better used by caulking windows. But better still adding R-60 roof insulation. Then residing with R-25 foam. New R-20 windows for cool people
Posted @ Tuesday, February 26, 2013 8:08 AM by Tapani Talo
Tapani, I disagree. I think money spent on testing helps us determine where to put the caulk / foam and identify areas of unseen / hard to get to leakage. Plus we can properly use the blower door for quality control during and at the end of each project.
Posted @ Tuesday, February 26, 2013 8:34 AM by Stefan P-C
Even in NEW construction, I have to personally walk the contractor through every window and other openings, make sure that vapor barrier is continious. Older buildings - all frmed openings simply OPEN.
Posted @ Tuesday, February 26, 2013 9:51 AM by Tapani Talo
Caulking is like bandaids. People think they have done something, when they really need 90% improvement with proper insulation to benefit and be safe and comfortable with no utility costs to talk about.
Posted @ Tuesday, February 26, 2013 10:05 AM by Tapani Talo
so once again, the answer is
it depends.

if you invest in a good caulk with a long life, install it properly it lasts. install cheap short life caulk improperly ...then it is a band aid.

insulation with no air sealing is a waste of money.

caulk is an excellent way to air seal leaks in homes
with above considerations.
just as mastic is an excellent sealant for ductwork.

the right product for the leakage site is what makes the work last.
Posted @ Tuesday, February 26, 2013 12:18 PM by Debbie
I am personally not a big fan (no pun intended, oh, ok, you got me) of extrapolation. From my experience, old homes over about 3000 sf are pushing the limits that I trust around 7000-8000 cfm50.

We just finished a 10,000 sf home built in 1913, and it had a 9930 blower door. As leaky as those homes usually are and as large as it is, I just can't see 1cfm50/square foot. That is typically close to Building Air Standard (sorry to bring it up, but it's still something to gauge against.)

My guess would be this house is closer to 15,000-20,000 cfm50. The program I work with only sends out 1 door, and I only have 1 door. I told the homeowner not to expect a big change in the number because I don't think it was accurate to begin with. I don't mean to be a wet blanket here, by the way, I'm just curious:

Do the blower door manufacturers out there have any verifications where extrapolation was done vs. 2-3 fans to get a real number? Do they match up? I'm betting Michael Blasnik has something... =)

I grant you there aren't many houses out there like this, but we have done 2. And yes, I should buy another blower door...
Posted @ Tuesday, February 26, 2013 3:30 PM by Nate Adams
I did a few bd's on a 10,000 SF national register house a while back. I could not get pressure on any of the tests and the varied cfm50 #'s didn't provide me any confidence in the readings. As we installed improvements and aligned the air barriers with the insulation, we did see marked improvements in the utility bill metrics though. They did not align with our pressure tests.
Posted @ Tuesday, February 26, 2013 6:57 PM by Chris Bellanca
My message went poof in the middle.
Accuracy of @ 50 Pa
1. decreases as distance between the test pressure and 50 Pa increases.
2. decreases as actual extrapolation value departs from the preset value of 0.65 in all gauges. If you have a leaky house, this value can be set to 0.55 to get better results. A feature on the Retrotec gauge and one that is not understood.
3. when it's windier the error will increase also.

Rule of thumb, don't go below 20 Pa and you'll be within 25% most of the time. Maybe 35%. If it leaks that much, it is either bad or super bad and needs to get fixed.
Posted @ Wednesday, February 27, 2013 4:56 AM by Colin
If you really want to see the accuracy play out, simply take cfm50 readings with @50 Pa turned on and run the gauge up from 10 to 50 Pa and not the values you get along the way. Different houses will give different results depending on what the hidden n is for that house. If you have no time for any other pursuits, change the n value in the gauge and you will find a value that gives the same results at all pressures. You will now be an expert.
Posted @ Wednesday, February 27, 2013 5:03 AM by CG
Thanks, Colin! That does help out and answers a question I don't have all that often... =)
Posted @ Wednesday, February 27, 2013 6:50 AM by Nate Adams
It blows my mind (pun intended) that the same crowd (the energy geeks) are trying to get blower doors, duct blasters, and bd frames small enough and/or tight enough to test Passive Houses accurately are simultaneously trying to figure out how many BD's we need to test 10,000 sq ft houses. Could there be a bigger disconnect?
Posted @ Wednesday, February 27, 2013 4:28 PM by Ryan Shanahan
Ryan - Point taken. My focus is older homes, not new ones. So high blower door numbers are my world. A customer just pulled a 3700 on a 1400 sf house. As much as I love Net Zero and PassivHaus, and they are the way of the future, there are about 100 million existing homes that need love out there. Including a few 10K sf ones.
Posted @ Wednesday, February 27, 2013 5:18 PM by Nate Adams
Nate, Point taken as well. I work exclusively with new contruction. I tend to see things through that lense. Keep fighting the good fight!
Posted @ Wednesday, February 27, 2013 5:43 PM by Ryan Shanahan
I don't know who "Debbie" is, but I think I like her.

CG too.

But it is most reassuring to do the numbers yourself. I have access to a similar sized house, and own a double drape. So I think when the weather get's better I'll borrow a second fan and test both ways.

I've always felt that once the number gets huge, accuracy of the cfm50 number becomes less critical. I do write down the actual Pa as well just for reference.

Nate, if you didn't get to 50, what number DID you get to? Anybody think it make sense to measure to that number as well as 50 when he is done?
Posted @ Monday, March 11, 2013 7:58 PM by ted kidd
 Post Comment Name  * Email  * Website (optional) Comment  * Allowed tags: link, bold, italics Receive email when someone replies. Subscribe to this blog by email.