A few months ago, I wrote about the confusing world of dehumidifier capacity. That quantity tells you how much water a dehumidifier will produce in a given amount of time. Here in the US, we use pints per day, but any volume per unit time will work. The efficiency of a room dehumidifier is another important quantity, although it gets far less attention. Dehumidifier efficiency is usually given as the amount of water produced per unit of energy used. And because we’re not completely backwards with regards to units here in the US, we use liters per kilowatt-hour (L/kWh) for that one.
Measuring dehumidifier performance
When you buy a dehumidifier, whether it’s a standalone room dehumidifier or a full-blown whole-house ducted dehumidifier,** you can get the specifications for it. I’ve got a room dehumidifier in my basement that came with the house I bought two years ago. It’s a GE model ADEL50LRL2 made in 2014. The 50 indicates a nominal capacity rating of 50 pints per day.
I looked up the efficiency in a spreadsheet of historical data for older dehumidifiers on the US EPA website. The rated capacity is 51.84 pints per day, and the rated efficiency is 1.85 liters per kilowatt-hour. But how does it really perform? I’m going to talk mostly about the efficiency, but I did take a quick look at the capacity. My data show that it really produces about 38 pints per day, but that’s with the dehumidifier running continuously.
Over a two month period this summer, I collected data on energy use and water produced by this little dehumidifier. I used the same bucket you saw in the photo of my hot water measurements for the volume of water produced. To measure energy, I used an Emporia Smart Plug,* one of my new favorite building science tools. I tracked my data in an Excel spreadsheet.
The official rated efficiency, called energy factor for older dehumidifiers like this one, is 1.85 L/kWh. I actually did measure 1.90 L/kWh one time, but that was an anomaly. I did the experiment in two separate runs. For three weeks, I measured the performance with the dehumidifier running nearly continuously. Then I measured it with the dehumidifier running intermittently. Here are the results.
As you can see, the averages are significantly below the rated energy factor of 1.85 L/kWh. When running continuously, it’s 16% lower. When running intermittently it’s 30% lower. The intermittent number is closer to what you’ll probably get in real-world results.
The effect of runtime
Let’s look at three graphs of data from my smart plug.* The first one shows the dehumidifier running continuously. When running, it uses about 485 watts of power. In one hour, it would use just less than 0.5 kilowatt-hour of energy. If it ran continuously all day, it would use close to 12 kWh of energy and cost me about $1.50.
But if you have a room dehumidifier running continuously, you probably ought to look into ways to reduce the humidity through air sealing or crawl space encapsulation. And get a more efficient dehumidifier. In my basement, the dehumidifier cycles on and off when I set it for an appropriate relative humidity. The graph below shows a medium rate of cycling. It comes on for 8 to 10 minutes, then goes off for 4 or 5 minutes.
That hurts efficiency because when the compressor goes off, the coil warms up and loses its ability to dehumidify. When the dehumidifier comes back on, it takes some time before the coil gets to its lowest temperature again.
Then there are times when the cycles are short. In the graph below, the dehumidifier gets 2 minutes of runtime at full power with a bit of time ramping up and another bit of time ramping down. Then off for 5 minutes before starting up and having to cool the coil all over again. Not good for the efficiency of a room dehumidifier!
The effect of settings and weather
There are two reasons for short cycling. The first is how you set the dehumidifier. When I first began this little experiment, I set the dehumidifier to 60% relative humidity. That’s when it was running continuously. What was the actual humidity level in the basement? In the low 50s. So I changed the setting to 65% and then 70%. I now leave it at 70% and that keeps my basement relative humidity at about 57%.
The lesson here: Don’t trust the reading on your dehumidifier! They can be very far off. I don’t need to keep the basement at 50% relative humidity. That’s a waste of energy. Plus, I work down there and currently don’t have air conditioning while the basement renovation is on hold until I finish the book. Running the dehumidifier more means lower humidity but higher temperature. (A dehumidifier mostly converts sensible to latent heat. The electricity used also gets converted to sensible heat.)
The second reason for the variation in cycle time is weather. On a hot sunny day, the dehumidifier runs less. I don’t have AC in the basement, but I do get some cool, dry air from the main floor coming down the stairs. When it’s hot outdoors, the AC upstairs runs and dehumidifies more so the basement dehumidifier runs less. At night or on cooler days, the AC runs less, the basement humidity is higher, and the dehumidifier runs more. Those are the best times for a dehumidifier to run, too, because converting that latent heat (humidity) to sensible heat (higher temperature) can make the air conditioner run more.
My basement is too humid now for a couple of reasons. I already told you I don’t have air conditioning there. Also, I do have an encapsulated crawl space, but overall the basement is still too leaky. Once my book is done, I’ll gut the whole basement and then install the InSoFast insulation panels (photo above) I’ve already bought, and air seal the heck out of the basement. Because, you know, a house doesn’t need to breathe.
But back to the subject of dehumidifiers. The efficiency of my room dehumidifier is about 1.3 liters of water for each kilowatt-hour of electricity used. How efficient are the best dehumidifiers? The Santa Fe Ultra line of dehumidifiers** are rated at up to 3.6 liters per kilowatt-hour. I’ll be testing one of those in the future.
Allison Bailes of Atlanta, Georgia, is a speaker, writer, building science consultant, and the founder of Energy Vanguard. He has a PhD in physics and writes the Energy Vanguard Blog. He is also writing a book on building science. You can follow him on Twitter at @EnergyVanguard.
* This is an Amazon Associate link. You pay the same price you would pay normally, but Energy Vanguard may make a small commission if you buy after using the link.
** This is an affiliate link for Sylvane. You pay the same price you would pay normally, but Energy Vanguard may make a small commission if you buy after using the link.
NOTE: Comments are moderated. Your comment will not appear below until approved.